Used for indoor & outdoor laying,The Cable can bear a certain laying traction,but can't bear the mechanical force from
outide.Single core cable can't be allowed to lay in the magnetic pipe . The Cable is used for fixed laying in the rated
voltage (U0/U)0.6/1KV,3.6/6KV & below for power transmission.
2.Product implementation standard:
GB/T12706-2002 Rated Voltage 1KV(uM=1.2KV) to 35KV(uM=40.5Kv) insulation electrical power & auxilary IEC60502-1997
Rated voltage 1-30kV Insulation electrical power cable & auxiliaries.
The Max.conductor working temperature: 70℃ Centigrade Conductor short circuit temperature : highest temperature
not more than 160℃ , the longest time not more than 5 seconds.
The min.bending radius of cable installation :
Table 1 :
|Item||Single core Power Cable||3 Cores Electrical Power Cable|
|No Armour||With Armour||No Armour||With Armour|
|The Min.bending radius of cable installation||20D||15D||15D||12D|
|The min.bending radius near connecting box & terminal cable||15D||12D||12D||10D|
|Note : "D" refers to outside diameter of electrical power cable.|
(2)Installation laying temperature :
Cable installation laying temperature not less than 0℃ Cable current-carrying capacity laying mode & basic parameters:
Air laying: enviromental temperature : 40℃ Soil laying: enviromental temperature : 25℃ Soil Thermal resistance
coefficient : 1.0.m/W Cable laying arrangments:
Single core calbe arrangment :Flat type. (adjacent space equals to cable outside diameter);
Packaging & Shipping
In coils, wooden drums, steel drums or steel-wooden drums.
We could producing according to the customers' requirements.